Nghiên cứu xử lý số sóng hài bậc 3, chế tạo relay bảo vệ chạm đất máy phát điện trong vùng công suất thấp
This article shows distribution model of the third harmonic of voltage in the winding of three phase salient pole rotor alternating-current synchronous generator (DMHW).The base on that to put forward a mathematical formula for formalize to process for physically, which occurs on winding of the generator by the third harmonic of voltage and called be Winding Characteristic Equation and it is abbreviated to WCE. These many different methods are based on WCE to protect the stator winding in the case of ground faults in high resistance grounded synchronous generator above. Using third harmonic of voltage to protect winding with standard ANSI 27/59NT 3rd harm by filter harmonic wave voltage measured at terminal or neutral. In the method, function of third harmonic of voltage has variable to be real power. But WCE could reject the variable by to algebraic subtract the third harmonic of voltage of the neutral transformer from the third harmonic of voltage of the third harmonic terminal transformer. It is possible to infer the third harmonic electromotive force(e3rd) from per unit length of the winding is equal, because the flux magnet of third harmonic wave swept them is similar in the magnetic field intensity. On the other hand, according to our calculations, sum of e3rd on the stator winding equal zero. Base of that, quotient of the third harmonic voltage at terminal and neutral exactly reflects the ratio of the area on the stator winding and the stator winding length , where occurs ground fault position. For this reason, we have proposed a protection formula, which it is non-dimensional.
Reality, with above principle, we have made a new equipment which is aimed to obtain a 100% protection of the stator winding in the case of ground faults on every power range [-40MVA; 110MVA] of the generator operation. The components of the equipment have origin of Siemens and Russian. And it has fitted up at the our Company, in October , 2012.
How to Cite
Vietnam Journal of Sciences and Technology (VJST) is an open access and peer-reviewed journal. All academic publications could be made free to read and downloaded for everyone. In addition, Articles are published under term of the Creative Commons Attribution-ShareAlike 4.0 International (CC BY-SA) Licence which permits use, distribution and reproduction in any medium, provided the original work is properly cited & ShareAlike terms followed.
Copyright on any research article published in VJST is retained by the respective author(s), without restrictions. Authors grant VAST Journals System (VJS) a license to publish the article and identify itself as the original publisher. Upon author(s) by giving permission to VJS either via VJS journal portal or other channel to publish their research work in VJS agrees to all the terms and conditions of https://creativecommons.org/licenses/by-sa/4.0/ License and terms & condition set by VJS.
Authors have the responsibility of to secure all necessary copyright permissions for the use of 3rd-party materials in their manuscript.